# اسئلة واجوبة في الهندسة الكهربائية

(مهــ نور ســة) #1

[CENTER]
هذا تكملة الموضوع
[FONT=Comic Sans MS][SIZE=2][COLOR=Blue] NO.2
MEANS TIME DELAY
NO.21
MEANS DISTANCE
NO.25
MEANS SYNCHRONISM-CHECK
NO.27
MEANS UNDERVOLTAGE
NO.30
MEANS ANNUNCIATOR
NO.32
MEANS DIRECTIONAL POWER
NO.37
MEANS UNDERCURRENT OR UNDERPOWER
NO.38
MEANS BEARING
NO.40
MEANS FIELD
NO.46
MEANS REVERSE-PHASE
NO.47
MEANS PHASE-SEQUENCE VOLTAGE
NO.49
MEANS THERMAL
NO.50
MEANS INSTANTANEOUS OVERCURRENT
NO.51
MEANS AC TIME OVER CURRENT
NO.59
MEANS OVER VOLTAGE
NO.60
MEANS VOLTAGE BALANCE
NO.63
MEANS PRESSURE (MECHANICAL PROTECTION)
NO.64
MEANS APPARATUS GROUND
NO.67
MEANS AC DIRECTIONAL OVER CURRENT
NO.68
MEANS BLOCKING
NO.69
MEANS PERMISSIVE
NO.74
MEANS ALARM
NO.76
MEANS DC OVER CURRENT
NO.78
MEANS OUT-OF-STEP
NO.79
MEANS AC RECLOSING
NO.81
MEANS FREQUENCY
NO.85
MEANS CARRIER OR PILOT-WIRE
NO.86
MEANS LOCK OUT
NO.87
MEANS DIFFERENTIAL
NO.94
MEANS TRIPPING
What do you know about Earth Leakage Circuit Breakers ELCB?
Earth Leakage Circuit Breakers ELCB)
4.3 Earth Leakage Circuit Breakers (ELCB)
A human operator may come in a direct contact with a live wire or he may touch a ****l-case of a leaky instrument. In either case, a current flows through the body of the operator to the earth. The amount of this current depends on the touch voltage and the human body resistance, which is a variable. A current exceeding a few tens of mill amperes through the body may prove to be fatal if permitted to do so for a long time. The Earth Leakage Circuit Breaker (ELCB) when installed in the electrical wiring protects the operator from such hazards. The ELCB is a safety device, which operates on low earth leakage current flowing in an electrical system. At such small currents, fuses or circuit breakers do not provide any protection, as they cannot operate till very high current flows in the wiring .
In USA and Canada, the same device (ELCB) is known as a Ground Fault Circuit Interrupter (GFCI) and in Europe it is called a Residual Current Circuit Breaker (RCCB). All these devices (ELCB, GFCI and RCCB) operate on the same principle [14].
In a typical wiring arrangement of an ELCB installation shown below , the live and neutral wires are passed through a magnetic core. Under the normal conditions, because the current in both conductors is equal and opposite, there is no flux in the core and the relay coil is de-energized. The electrical supply to the load equipment is not interrupted.
Life neutral
under certain fault conditions (e. g. leakage due to a faulty insulation), the current in the live wire can exceed the neutral wire. This produces flux in the core. The secondary winding on the same core produces a voltage, which is amplified and applied to a relay coil. The relay operates and interrupts the live and neutral conductor. The earth leakage trip current can be pre-adjusted between 5 mA to 30 mA depending on the application in which it is used.
A typical ELCB is built into a 230-volt circuit breaker and is located in the panel board. A reset lever is provided on the ELCB to reset it after the cause of the leakage is detected and removed. A test button, if provided on an ELCB, can be pushed to check the functioning of the device as this action simulates an imbalance in the live and the neutral wire.
In the three-phase ELCB variety, the vector sum of the currents in the three lines and the neutral is continuously monitored. A nonzero current indicates a leakage in the wiring and the ELCB operates and disconnects all the supply conductors of the equipment [15].
The technical data of a typical ELCB device available in the Indian market is shown in the Table 4.3 [15] below:
Table 4.3: Technical Data of an ELCB
Specifications
BS 4293 – 1983/IS12640 – 1988
Sensitivities
High (30 mA)
Medium (100 mA)
Low (300 mA) Optional
Normal Voltage
2Pole 240 VAC 50 Hz
4 Pole 240/415 VAC 50 Hz
Electrical Life
4000 operations
Mechanical Life
20,000
Connection Capacity
25/40 A – 16 sq. mm
63/80 A – 25 sq. mm
100 A – 35 sq. mm
Ambient Temperature Range
50C to ȴ00 C
Degree of Protection
IP 30
Recommended Back-up HRC fuses
for 25 A & 40 A
80 A
for 63 A, 80 A & 100 A
100A
Installation of an ELCB for a domestic environment and that for a number of equipment that performs a variety of unrelated functions in a field station can differ considerably. A tripping of a single ELCB need not bring to a halt the operation of the entire field station till the cause of the trip is located and rectified. For this, the equipment in the field station is divided in clusters and a separate ELCB is installed for each of them. This allows a majority of operations in a field station to continue in case an ELCB trips the supply to a group of equipment in a cluster.
ELCBs are available from following suppliers:
• Siemens Ltd., Bombay
• MDS Switchgear Ltd., Bombay

What is meant by 100% (S/E/F)in the generator protection
(ANSI 64G-100%)? and give two methods of how to do that?
means 100% Stator Earth Fault, and this protection covers the entire widing by detecting the ground faults that may occur near the neutral end of the stator winding.
the two basic methods:
1- use of the third-harmonic voltage, or
2- the injection of a subharmonic voltage.
What are the P.T & C.T tests?
for the P.T *
types of P.T
core type & the capacitor type
THE TESTS ARE
1- insulation test
2-error test
in this test we found on the p.t manual that it’s error test =+3 or 3p
and that means that error = 3%
there is the turns ratio test&
types of P.T
core type & the capacitor type
*for the C.T
saturation test
in this test we apply voltage in the primary & check the secondary current
& it’s written on the c.t manual as
1500/5
1500…is the primary applied voltage
5…the secondary current
error test
it’s written on the c.t manual as
5p20
5p=5%
20=20 * rated current
insulation test
we measure the resistance to check the insulation
Q: WHAT IS THE DIFFERENCE BETWEEN ‎PRIMARY INJECTION AND
SECONDARY ‎INJECTION FOR PROTECTION RELAYS
primary injection is carried out with ‎full rated current of the circuit by ‎using a.c current source and ‎injecting it in the primary side of the ‎current transformer of circuit

secondary injection is carried out at ‎secondary side of ct by injecting ‎secondary current in to the relay to ‎prove the function and operation and ‎setting of the relay by special ‎testing set.

what’s the principle operated the main protection relays should be considered on the (ATS function between normal power supply and emergency power supply)
2.1 Automatic Transfer Operation
2.1.1 Summary
In general, the automatic transfer operation is initiated if a low voltage is detected on incoming Line A. When initiated, the ATS will simultaneously check for these four conditions: a) both incoming breakers are closed and in operating position; b) the bus tie breaker is open and in operating position; c) incoming breaker 52-A is not carrying fault currents; d) voltage on Line B is adequate and has been adequate for at least a set duration. If all four conditions are satisfied, the ATS will open incoming breaker 52-A. The ATS will then check to ensure that the residual voltage on the switchgear Bus A is at a safe level. If Bus A residual voltage is at a safe level, the ATS will close the bus tie breaker, allowing the whole switchgear to be supplied from incoming Line B. Otherwise, automatic transfer is blocked and operator intervention will be needed to reset and return the ATS to its normal position.
2.1.2 Detailed Sequence of Operation.
The under voltage relay device 27-A monitors the voltage on incoming Line A. This relay shall be of the induction type, equal to GE type IAV54EIA or ABB Type CV-2 short-time. It shall be set so that it does not pick up on ground faults in a high resistance grounded system. The recommended setting is 45% of nominal voltage, with a time delay of 20.
If a low voltage is detected, the under voltage relay device 27-A initiates the automatic transfer operation mode of the ATS. Low voltage on incoming Line A is due to various reasons. It may be due to a voltage depression at the upstream supplying bus. For the case where incoming Line A is without a transformer, it may be due to a fault on the line between the upstream supplying breaker and the incoming breaker 52-A. For the case where Line A is with a transformer, it may be due to: a fault on the line between the upstream supplying breaker and the transformer; a fault in the transformer primary winding; a fault in the transformer secondary winding; a fault in the transformer pressure; or a fault on the bus duct between the transformer and the incoming breaker 52-A. Or, it may be due to a fault downstream of incoming breaker 52-A.
When initiated, the ATS simultaneously performs the following verifications:
المحولات اعلاه تستخدم في شبكات توزيع الكهرباء
وضع لنك فيوز مع سلك مناسب للفيوز
موازنة الاحمال على اطوار المحوله
وضع مانعة صواعق
الحمل المطلوب لا يتجاوز 80%من حمل المحوله
صيانة المحوله بشكل متواصل[/color][/size][/font]
How do the circuit breaker and relay operate?
[FONT=Comic Sans MS][SIZE=2][COLOR=Blue]Circuit breaker and relays step by step operating procedure while isolating a fault (the time intervals between each event will be in the order of a few electrical cycles i e milliseconds.
The relay receives information which it analyses and determines that the circuit should be opened
Relay closes its contacts energizing the trip coil of the circuit breaker

The C.B is unlatched and opens its main contacts under the control of the tripping spring.
The trip coil is de energized by opening of the circuit breaker auxiliary contacts

Q: WHAT ARE THE MAIN GENERATOR ‎PROTECTION RELAYS FOR GENERATOR >120 ‎MW? ‎
THE MAIN GENERATOR PROTECTION ‎RELAYS ARE THE FOLLOWING
STATOR EARTH FAULT RELAY
ROTOR EARTH FAULT RELAY‎
GENERATOR DIFFERENTIAL RELAY
GENERATOR OVER VOLTAGE RELAY
GENERATOR UNDER VOLTAGE RELAY
GENERATOR UNDER FREQUENCY RELAY
NEGATIVE PHASE SEQUENCE RELAY
LOSS OF EXCITATION RELAY
GENERATOR OVERCURRENT RELAY
REVERSE POWER RELAY.

How do you carry out C.T ratio test? ‎
‎1. Connect the C.T as indicated in ‎figure 1.‎
‎2. Start the AC current source and ‎inject 25%, 50%, 75%, and 100% of ct ‎primary current rating
‎4. The ratio of a1 to a2 should ‎approximate to ratio marked on ‎the current transformer ‎nameplate.‎
HOW DO YOU CARRY OUT POLARITY TEST ‎FOR C.T? ‎
‎1. CONNECT THE C.T IN THE CIRCUIT AS ‎SHOWN IN FIG 1.THE AMMETER SHOULD ‎A ROBUST MOVING COIL PERMANENT ‎MAGNET CENTER ZERO TYPE
‎2. PRESS THE PUSH BUTTON AND SEE THE ‎DEFLECTION IN THE AMMETER.‎
‎3. THE AMMETER SHOULD GIVE POSITIVE ‎FLICK ON CLOSING THE CIRCUIT AND ‎NEGATIVE FLICK ON OPENING THE ‎CIRCUIT.‎
WHAT IS THE C.T AND P.T
CT IS CURRENT TRANSFORMER ‎
PT IS VOLTAGE TRANSFORMER

What are the main tests carried out ‎for current transformer before ‎commissioning? ‎
‎1. Polarity test‎
‎2. Magnetization curve
‎3. Ratio check
What are the main tests carried out ‎on pt before commissioning? ‎

1. Polarity check‎
‎2. Ratio check‎
‎3. Phasing check.‎
What is the main function of ‎protective relay?
The protective relay senses the ‎abnormal condition in a part of the ‎power system and gives an alarm or ‎isolate that part from the healthy ‎system by opening the circuit breaker ‎feeding that part.‎
What is the difference between ‎primary and secondary protection?
Primary protection is the first ‎protection to act and backup ‎protection is the next in the line of ‎defence. If the fault did not clear by ‎primary protection back up ‎protection comes in picture and clear ‎the fault.‎
What are the types of circuit breaker ‎based on arc quenching medium?
THE CLASSIFICATION OF CIRCUIT BREAKERS ‎BASED ON THE MEDIUM OF ARC ‎EXTINCTION IS AS FOLLOWS:-
‎1. AIR CIRCUIT BREAKER AND MINIATURE ‎CIRCUIT BREAKER.‎
‎2. OIL CIRCUIT BREAKER.‎
‎3. MINIMUM OIL CIRCUIT BREAKER.‎
‎4. AIR BLAST CIRCUIT BREAKER.‎
‎5. SULPHUR HEXAFLUORIDE CIRCUIT ‎BREAKER (SF 6).‎
‎6. VACCUM CIRCUIT BREAKER.‎
What is the meaning and function of ‎HRC fuse? ‎
HRC fuse is high rupturing capacity ‎fuse and its function is to protect the ‎electrical circuit from excessive ‎current due to overload and or ‎short circuit.
Why the secondary of the ct should ‎never be left open.‎
The secondary of the ct should ‎never be left open as the dangerous ‎high voltage will be developed due ‎to the absence of un opposed mmf. this ‎is the reason why wherever ‎secondary ct circuits are used there ‎is always a facility provided for ‎short circuiting the secondary.‎
Why the secondary of the ct should ‎never be left open.‎
The secondary of the ct should ‎never be left open as the dangerous ‎high voltage will be developed due ‎to the absence of un opposed mmf.this ‎is the reason why wherever ‎secondary ct circuits are used there ‎is always a facility provided for ‎short circuiting the secondary.‎
What are the tests to be performed ‎on CT’s ?‎
A) C.T ratio test: this test is ‎important to conduct because ‎the ct gives the true replica of ‎primary current.‎
B) C.T polarity test: test of polarity ‎is important otherwise wrong ‎polarity may result in to ‎spurious tripping.‎
C) C.T saturation test: if the ct is ‎saturated it will not offer a ‎correct information about the ‎primary current. This situation ‎normally occurs when ct has ‎handled a large fault currents.‎

what will you predict about the ‎transformer if the vector group ‎mentioned is dy5? Explain ‎thoroughly? ‎
the vector group represent the ‎manner in which the two windings are ‎connected and phase position of the ‎respective voltage vectors.
The ‎capital letter indicates the ‎connection of high voltage ‎windings. Here high voltage winding is ‎connected in delta and small letter ‎indicates connection of LV winding ‎which is star in this case.
The no 5 ‎indicates the angle between HV and ‎LV vectors on a clock.i.e,150 degree ‎LV WDG vector lags behind that of ‎HV winding.‎

WHAT ARE THE PROTECTIONS FOR THE ‎FOR THE FOLLOWING ELECTRICAL ‎EQUIPMENT’S.?‎
A. GENERATOR
B. TRANSFORMER
A). GENERATOR
OVER CURRENT / EARTH FAULT / ‎INSTANTANEOUS RELAY
DIFFERENTIAL RELAY
REVERSE POWER RELAY
FIELD FAILURE RELAY
BEARING/WINDING /OIL TEMPERATURE ‎RELAY

B). TRANSFORMER
OVER CURRENT RELAY
DIFFERENTIAL RELAY
BUCHHOLZ RELAY
WINDING /OIL TEMPERATURE RELAY
OIL LEVEL; RELAY
What are the main protection relays ‎for ac motors? ‎
the main protection relays for AC ‎motors are
‎2. Earth fault relay‎
‎3. Over current relay‎
‎5. Locked rotor relay

Explain how protective relays are ‎primary injection tested?‎
The primary of the current ‎transformer is connected to the ‎primary injection test kit and the ‎current is slowly increased.
The pick ‎up /operating current of the relay is ‎checked.

Describe the principle of directional ‎over current relay?
Directional over current relay ‎responds to over currents for a ‎particular direction flow.
It ‎comprises over current relay and ‎power directional relay.

‎What is circuit breaker? ‎
a device that is designed not only to ‎open and close non automatically ‎but also to open the circuit ‎automatically at a predetermined ‎current and overload values.
What is a feeder ?‎
the circuit conductors between the ‎service entrance equipment or ‎isolated generating plant and the ‎branch circuit overload device

What does an isolating switch mean?‎
a switch that is intended for ‎isolating an electric circuit from its ‎source of power .it is intended to be ‎operated only after the breaker has ‎been opened by some another means
What is meant by 5p20. 1m5 ?‎
‎5p20 denotes the accuracy class of ‎protection class ct 5% error and 20 ‎times saturating current…

What precautions must be taken ‎when working with current ‎transformer? Why? ‎
the secondary of the ct must never ‎be opened when the primary circuit is ‎energized. if it is necessary to ‎disconnect an instrument while the ‎circuit is energized the secondary of ‎the c.t. must be shorted, otherwise ‎the potential of the secondary may ‎reach dangerous values causing ‎damage of the c.t. but by short ‎circuiting of the secondary damage ‎is avoided.‎
What is the polarization index and ‎how much it should be for a.c. ‎machines ?‎
polarization index is the ratio of ‎insulation reading for 10 minutes ‎over insulation reading for 1 minute.‎
ir value for 10 minutes /ir value for 1 ‎minute

How do you carry out polarity test ‎for ct ? show by drawing?‎
when closing switch the meter gives + ‎reading.when opening the switch ‎meter gives - reading ‎

What is the difference between ‎primary and secondary injection ‎test? draw circuit?‎
primary injection of the relay is ‎carried out to prove the total ‎circuit before start up is okay.we ‎normally inject 2 to 3 times rated ‎current to prove the circuit.‎
secondary injection is done from the ‎secondary side of ct or pt to check ‎the healthiness of the relay.‎

What is phase angle ?‎
it is the electrical angle degree ‎between 2 vector i & v(30*)

Why dc system is not grounded. ‎explain?‎
for reliable operation. if a circuit ‎gets grounded it will go out of ‎service immediately.‎

Why the ground fault is to be ‎cleared quickly ?‎
circuit may energize without the ‎knowledge of operators

What is meant by hi-pot test? ‎
this is nothing but a high voltage ‎test conducted on ht electrical ‎equipments to check the quality of ‎insulation.
What is the difference between core ‎balance ct and zero sequence ct ?‎
both are same.‎
How a clamp meter or clip on meter is ‎used for 3 phase load current ‎measurement ?‎
the meter should be clamped one by ‎one core and individual phase ‎current should be measured.the ‎meter should not be clamped in all ‎three cores at the same time.

Why over current relays are not ‎used to protect motors.‎
Over current relays does not follow ‎the heating characteristic of ‎motors. Only thermal o/l relays does ‎this.

What an I.D.M.T. relay means?
Inverse definite minimum time lag relay.‎
What is meant by phase sequence ‎‎? How do you reverse it? ‎
the phase sequence is the cyclic ‎order in which the voltage wave ‎changes their peak.correct phase ‎sequence=r-y-b.reversed phase ‎sequence=rby.this can be obtained by ‎reversing b & y phases.
What are the basic protections in ‎a moulded case circuit breaker?‎
‎1. thermal protection
‎2. short circuit protection
Where is a moulded case circuit ‎breaker preferred and where is ‎fuse protection preferred ?‎ ‎

fuse protection is mainly used ‎only for short circuit protection ‎and does not provide overload ‎protection.‎
‎ a moulded case circuit breaker ‎gives both overload and short ‎circuit protection. for heavy loads ‎moulded case circuit breaker is ‎more economical than fuses. ‎
‎ fuses need frequent replacement ‎while moulded case circuit ‎breaker does not need frequent ‎replacement.‎

What is a single phasing preventer ‎‎? ‎
this will protect the motor if any ‎one of the three phases is open ‎circuited.‎
Q: choose the correct answer? Three phase faults are generally ‎faults‎
‎1. Symmetrical‎
‎2. Unsymmetrical‎

symmetrical
How a clamp meter or clip on meter is ‎used for 3 phase load current ‎measurement? ‎
the meter should be clamped one by ‎one core and individual phase ‎current should be measured. The ‎meter should not be clamped in all ‎three cores at the same time.
Q: how can the distance relay differentiate between a fault and a power swing

By the following criteria

1. Fault make the impedance measured by the relay to fall rapidly, power swing is somehow slow
2. in the case of power swing the impedance will not settle inside the trip c/c’s of the relay it will get back to the outer zone or continue to the other side of the c/c’s that means the system is out o f step
3. in the case of power swing , it’s symmetrical, no negative or zero sequence exists in this case
in the case of a fault, zero sequence or negative sequence is present except for symmetrical faults

FOR GENERATOR TRANSFORMER(DELTA-STAR CONNECTION) DIFFERENTIAL RELAY.
WHY WE COONECT THE CT IN THE DELATA SIDE IN STAR &IN STAR SIDE WE CONNECT IN DELAT

من المعلوم ان التوصيل بهيئة دلتا استار للمحولات
-1 الدلتا تمنع مرور تيار التتابع الصفري …

[/color][/size][/font]2- يتكون انزياح طوري بين الدلتا والنجمة[FONT=Comic Sans MS][SIZE=2][COLOR=Blue]

اذا لو افترضنا ان محول الطاقة موصل على هيئة دلتا نجمة 11،
فانه يجب ان توصل محولات التيار كالآتي :

جهة الدلتا لمحول الطاقة نجعل توصيل محولات التيار نجمة
وجهة الأستارلمحول الطاقة نجعل توصيل محولات التيار دلتا.

ونجعل التوصيل في ما بين محولات اليتار على هيئة نجمة دلتا 11
وبهذه الطريقة يعدل الأنزياح الطوري الناشىء بين الملف الأولي والملف الثانوي لمحول الطاقة،
ونمنع التيار الصفري من المرور في دائرة محولات التيار …

## وبس[/color][/size][/font] FAULT CONDITION ‎ ‎ ‎ [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]1- OHL 2- BUS ISOLATOR 1, 2 OPEN 3-C.B OPEN 4-LINE ISOLATER CLOSED 5- FAULT BETWEEN LINE SIDE C.T &C.B WHICH PROTECTION CLEAR THE FAULT

THE END FAULT PROTECTION WILL CLEAR THE FAULT BY SENDING
TRIP COMMAND TO REMOTE END C.B .
THIS FEATURE END FAULT IN THE BRF RELAY

Q- BOTH BUS ISOLATOR Q1& Q2 CLOSED THERE IS FAULT ON BUS BAR WHAT WILL HAPPEN
1- ALL SUBSTATION WILL TRIP )BLAKOUT)
IN CASE OF Q1&Q2 IT CALLED CROSSCOUPLED &THE BB 2 DIFF RELAY WILL BE THE MASTER .THROUGH CROSS COUPPLED TRIPBUS 1,2 WILL BE ONE BUS & ALL FEEDERS WILL TRIP

CONDTION REDAIL SUSBSTATION A FEEDING FROM

SUBSTATION B THROUGH OHL LINE
FAULT VERY CLOSE TO S/S B
HOW DISTANCE CLEAR THE FAULT IN S/S A
THE FAULT WILL BE CLEAR BY F21 IN S/S A BY WEAK INFEED FEATURE AND RECLOSE SUCCFULLY
WHAT IS THE CONDTION OF WEAK INFEED
1- CURRENT IS VERY LOW & RELAY CAN NOT START
2-THERE IS VOLTAGE DROT 30%
3-NO START IN REVERSE SIDE
4-THERE IS CARRIER RECIVE FROM STRONG END
5-C.B IS CLOSED

Q- What will happen in case of any phase voltage = o for distance relay
Distance relay will be blocked after 10 sec & it will run in emergency o/c mode
this feature is called fuse fail condition
there 2 conditions for this case
1- fault within 10 sec
the distance will operates as normal
2- fault after 10 sec passed
the fault will be cleared by O/C mode after 2.5 sec distance will be blocked

Q :What is the IP standard "Protection degrees of enclosures
كل جهاز او معدة يكون لها IP وهو درجة الحماية لهذه المعدة حيث يكون مكون من ثلاث ارقام[/color][/size][/font] ex. IP 543
[FONT=Comic Sans MS][SIZE=2][COLOR=Blue]
الرقم الاول “5” وهي درجة حماية الجهاز من dust
الرقم الثاني “4” وهي درجة حماية الجهاز من "water or "liquid
الرقم الثالث “3” وهي درجة حماية الجهاز من mechanical impact

وهناك درجات حماية مختلفة لكل رقم

وناخذ في الاعتبار ان احيانان الرقم الثالث لا يكتب وذلك يوضح ان هذه الماكينة محققة mechanical impact

What is the breaker failure?
The breaker failure relay is used when the fault happened on transmission line or power transformer and the breaker is not open to clear fault even if the protection relays sent the trip signal to the circuit breaker but the circuit breaker fail to open.
The breaker failure sense two factors the fault current and receiving trip signal from protection relays of the transmission line or power transformer the breaker failure have delay time after receiving the trip signal from protection devices about 150 ms to ensure that the circuit breaker is open if it is not open and sense also there is still fault current the breaker failure make retrip to the same circuit breaker if not open the breaker failure have 200 ms delay time then make trip for all feeders and the power transforms that sharing this transmission line or power transformer that circuit breaker fail to open at the fault case the trip go through the bus bar replica to clear all feeders that share the faulty cb feeder.

Q1. How deep must I bury USE cable?
A1. When cables or raceways are run underground, they must have a minimum “cover” in accordance with Table 300.5. Note 1 to Table 300.5 defines “Cover” as the distance from the top of the underground cable or raceway to the surface of finish grade. According to this table, Type USE cable must have 24” of cover, unless the installation is a residential 15 or 20A branch circuit rated 120V or less with GFCI protection.

Q2. Can low-voltage Class 2 thermostat wire be installed in the same raceway with power conductors for the a/c compressor?
A2. No, 725.55 specifies that Class 2 cables are not permitted to be placed in any enclosure, raceway, or cable with conductors of electric light or power.

However, Exception No. 2 to 725.52 allows Class 2 circuits to be reclassified as a Class 1 circuit if the Class 2 equipment markings are eliminated and the circuit is installed in a Chapter 3 wiring method [725.55(D)(2)(b)]. Reclassifying the circuit allows the Class 1 circuit to be installed with functionally associated power circuits in accordance with 725.26(B)(1). Figure 725-30

Q3. Can Type MC cable be installed in a cable tray?
A3. Yes. See Table 392.3(A).

Q4. Can I use a cable tray in a commercial occupancy?
Q4. Yes, cable tray installations aren’t limited to industrial establishments [392.3].

Q5. How do I size the circuit conductors and protection device for a 25 hp, 208V three-phase fire pump motor?
The fire pump motor circuit overcurrent protective device must be sized to carry indefinitely the sum of the locked-rotor current of the fire pump [695.4(B)(1)]. According to Table 430.251(B), the locked-rotor current of a 25 hp, 208V, three-phase motor is 404A. This requires a 450A protection device, in accordance with 240.6(A).

Conductors supplying a fire pump motor must must have an ampere rating of not less than 125 percent of the fire pump motor full-load current (FLC), as listed in Table 430.248 or 430.250. The FLC of a 25 hp, 208V, three-phase motor is 74.8A, so the conductors must be sized no smaller than 93.5A (74.8A x 1.25). According to Table 310.16, we can use a 3 AWG rated 100A at 75°C [110.14©(1)].

Careful, the branch-circuit conductors for a fire pump motor must be sized so that the voltage at the line terminals of the controller, when the motor starts (locked-rotor current), does not drop more than 15 percent below the controller’s rated voltage. In addition, the voltage at the motor terminals must not drop more than 5 percent below the voltage rating of the motor when the motor operates at 115 percent of the fire pump full-load current rating.

Q6. Can liquid tight flexible ****l conduit be installed under the raised floor of a computer room and if yes, must it be secured?
Branch-circuit supply conductors for information technology equipment can be installed in liquid tight flexible ****l conduit located under a raised floor. And yes, the raceway must be securely fastened in place [645.5(D)(2)].

Q7. Can I ground a satellite system to the ****l parts of electrical equipment?
A7. No. The antenna mast [810.15] and antenna discharge unit [810.20©] must be grounded to one of the following:

Building or structure grounding electrode system [250.50]
Interior ****l water piping system, within 5 ft from its point of entrance [250.52(A)(1)]
Accessible means external to the building, as covered in 250.94
****llic service raceway
Service equipment enclosure
Grounding electrode conductor or the grounding electrode conductor ****l enclosure
Grounding the lead-in antenna cables and the mast helps prevent voltage surges caused by static discharge or nearby lightning strikes from reaching the center conductor of the lead-in coaxial cable. Nothing can prevent damage from a direct lightning strike. But grounding with proper surge protection can help reduce damage to satellite and other equipment from nearby lightning strikes[/color][/size][/font][/center]

(مهــ نور ســة) #2

[CENTER][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]-1ظهور فولت من 0الي110فولت علي خط النيوترال في انظمة ال3 فاز[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] -2فصل خاطيء وغير منطقى للC.Bواحتراق فيوزات الحماية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] -3اتلاف مؤقتات التاخير في الريليهات (UNDER VOLTAGES)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] -4حرق مكثفات تحسين القدرة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 5[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=Blue]- زيادة الفقد الكلي في الطاقة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 6- كسر عزل خطوط النيوترال او التسبب في اشتعال الحرائق في الكابلات حتي الممدود منها داخل مواسير[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] (Q)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 7- حدوث تداخل في شبكة الاتصالات 8- سخونة عالية في الاحمال الغير خطية(مواتير-لمبات نيون-ملفات الخنق…) 9- احتراق الاجهزة الاليكترونية الحساسة[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] كيفية تكونها[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] اي تشوه في الفولت او التيار يسبب حدوث التوافقيات بحيث يتم جمع تردد الموجة الاصليةمع تردد التوافقيات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الثالثة والخامسة…ويؤدي ذلك الي تشوه الموجه الاصليه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] بنشأ ذلك بالاساس في انظمة 3-PHASE التي من المفترض ان يكون النيوترال فيها ليس عليه اي فولت لان [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] مجموع ال 3 مركبات للموجة الاساسيه = صفر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الاجهزة المسببة للظاهرة[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .1مغيرات السرعة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .2المحولات-المواتير[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .3الاجهزة الكهربية المحتوية علي ثايرستورات مثل اجهزة( (DVD-AUDIO/VEDIO AMPLHFIER[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .4اللمبات الفلورسنت-ملفات الخنق(جميع انواع الdischarge gas lamps)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .5ماكينات اللحام الكهربي-افران الاقواس الكهربية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .6مفاتيح الفصل و التشغيل (لمدة صغيرة جدا وهي لحظة الفصل والتشغيل([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .7اجهزة الكومبيوتر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] العلاج[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] تركيب ملفات ال detuned في وحدات تصحيح معامل القدرة الاوتوماتيكى(VARLOGIC)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: انواع محولات التأريض.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] محول الزجزاج [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] محول ألـ open delta[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] المحولات 1و2 تستخدم في محولات الدلتا [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] محول المعاوقة العالية … وتستخدم في تأريض المولدات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يوجد ملاحظة على البند رقم 2 و هى ان وظيفة توصيلة الـ open delta ( تسخدم فى محول الجهد )[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] هى الحصول على جهد المركبة الصفرية فى حالة حدوث قصر بين احد الأوجه و الأرض لاستخدامة فىتحديد اتجاه تيار القصر فى الوقاية المسافية او الوقاية من زيادة التيار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ما هى عملية ''Reclosing"[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] عند حدوث خطأ فى منظومة القوى الكهربيه فان المرحل يشعر به وبالتالى يقوم القاطع بفصل الدائره،ولكن كثير من الأخطاء التى تحدث فى المنظومه تكون ذات طبيعه مؤقته Temporary بما يعنى أن القاطع اذا تم توصيله مرة أخرى فيمكن أن يكون الخطأ قد زال بدون عمل أى اجراء،ولهذا فان المرحل يعيد توصيل القاطع بعد فتره زمنيه محددة فاذا كان الخطأ قد زال تعود الدائره للحاله العادية واذا كان الخطأ مازال موجودا يتم تشغيل القاطع وفصت الدائره مره أخرى وتكرر العمليه السابقه لمه أو مرتين ويمكن أن تكون عملية اعادة التوصيل الألى سريعه (حوالى 1ثانيه) أو بطيئة حسب نوع الخطأ ومكانه ،ولكن يجب مراعاة ألا تتكرر هذه العملية عدة مرات للحفاظ على سلامة وأمان المنظومه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]ups system .8[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س : كيف استطيع التأكد من ان الزاوية بين كل طور وطور متساوية القيمة باستخدام CLAMP METER ؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] نقيس التيار في كل طور للتأكد من قيمة التيار في كل طور ثم بعد ذلك نقيس الاطوار الثلاثة مجتمعة ولابد ان تكون النتيجة صفر 0 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] او نقيس طورين فقط مع بعض والنتيجة تكون قيمة الطور الثالث 0[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: هل يمكن حساب الجهد الذي يحدث عنده Knee Point في محولات التيار اي معرفة الجهد بطريقة حسابية تساوي تقريبا الجهد من منحنى التشبع[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ال Knee Point هي النقطة التي اذا ازداد الجهد عندها 10 % يزداد التيار بمقدار 50 % في محول التيار و بعد هذه النقطة يدخل محول التيار في التشبع[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الحساب التقريبي ل Knee Point :[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] لو عندنا محول تيار بياناته كالتالي :[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] C.T.R = 300/5 , Is=5 A , 5 P 10 , 60 VA [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] Knee Point = 1060 / Is = 1060 / 5 = 120 Volt[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] و للتوضيح 5P10 الرقم 10 يسمى [Accuracy Limit Factor ]و هو اقصى تيار يمر في محول التيار و تظل نسبة الخطأء كما هي عندما تكون الاحمال على دوائر الثانوي تساوي Rated burden[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] Vcallculated = ( ALF*Rated burden ) / In [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=Blue]حيث[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] I[FONT=Comic Sans MS][SIZE=2][COLOR=Blue]n = nominal secondary current[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ما هي الأخطاء الكهربائيه الرئيسية التي تحدث داخل شبكات النقل ؟…[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .2 دوائر القصر / تماس مباشر بين الاطوار او بينها وبين المحايد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .3 الدوائر المفتوحة /قطع في احد الاطوار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] .4 العازلية _تماس بين الاطوار والارض[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] 1. زيادة الحمل. [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ما هى الأعمال التي لا تحتاج إلى قطع القوة الكهربائية في محولات عالية القدرة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فحص المحولات من الخارج[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فحص العوازل… بواسطة (الميجر ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] قياس التيار …بواسطة (كيلامب اميتر) [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] اخذ عينة من الزيت واضافة الزيت الناقص[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فحص اغلفة الاجهزة الخارجية دريد العاني[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ماذا يحدث اذا قطع ال pilot cable قبل حدوث عطل فى ال power cable فى حالة وجود pilot [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] protection relay siemens relay 7SD600 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فى هذة الحالة يعمل الجهاز as EMG. O/C with time delay وليس pilot relay[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] كيف يمكن التغلب على مشكلة عدم وجود ملف ثانوى لمحول الجهد open delta فى حالة الرغبة فى تركيب جهاز وقلية اتجاهى ضد القصر الارضى DE/F [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فى هذة الحالة يمكن الاستعانة interposing VT عن طريق اخذ توصيلة النجمة من محول الجهد وادخالها على ال interposing VT من ناحية الابتدائى والخرج يكون توصيلة الدلتا المفتوحة يمكن استخدامها لل DE/F هذة الطريقة موجودة هنا فى الخدمة منذ مدة طويلة واظن على حد معلوماتى انها هى الطريقة الامثل التى تسمى STAR/DELTA CONVERTER واظنها مناسبة ايضا للسؤال الخاص بتوصيل العدادات الذى تفضل بة السيد المهندس الفاضل سعيد ابو خطوة وارخص من المقاومات الحرارية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ماهى الإختبارات التى تتم على محولات التيار داخل محطات التحويل ؟[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يبتم عمل الإختبارات التالية لمحولات التيار بالموقع [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - عمل إختبار قياس مقاومة الملف الثانوى DC RESISTANCE[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] -عمل إختبار القطبية POLARITY TEST[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] -عمل إختبار منحنى التشبع SATURATION TEST [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - عمل إختبار قياس عزل الملف الثانوى mugger test[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: يراد تركيب عدادات قياس الطاقه الكهربائيه DIGITAL METER HOUR MTER بخلايا الجهد المتوسط MV بالموزعات DP وخصوصاً [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] خلايا الدخول وعند تركيب العدادات تلاحظ أن جميع محولات الجهد المركبه عدد 2 بول [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] أى بنظام )V CONNICTION 3 WIRE PT) علماً العدادات METERS 4 WIRE [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ماهى الطريقه المثلى للتغلب على تحويل توصيلات محولات الجهد إلى رباعية الأطراف حتى يمكن [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] قياس جهد PHASE VOLTAGE بدون إستبدال محولات الجهد لتقليل التكلفه وعدم إحداث نسبة خطأ فى قرائة العدادات [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] تم التغلب على هذه المشكله وذلك بعمل الآتى :[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] تم شراء مقاومات حراريه قدرة المقاومه 7 وات THE POWER OF RESISTANCE 3 W.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] قيمة كل مقاومه 28 كيلو أوم- بعد إجراء عملية الحسابات [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] تركيب عدد 3 مقاومات لكل جهاز عدادوموصله بنظام STAR CONNECTION[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] توصيل أطراف الجهد الثلاثه على المقاومه والجهاز ( ممكن أن يكون جهاز وقايه - أوعداد)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وبعد ذلك تم تركيب نقط التعادل بالجهاز - وبالمعايره تبين عدم حدوث أى نسبة خطأبالعداد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وهذى الطريقه ممكن تسميتها (STAR / DELTA CONVERTER)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: لا ينصح بترك محول التيار مفتوح الداره عند الملف الثانوي اذ تتكون فولتيه عاليه [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] سؤالي هو لماذا تنشأ فولتيه عاليه وكيف يتم حسابها؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] the answer is according to what I want where the advantage of primary side is maintaining ampere turnes so burden will be maintaned without change but the disadvantage is decreasing short circuit level. and the the opposite advantage and disadvantage for changing ratio from secondary side[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=Blue] my question is if I have current transformer has facility to change ratio from primary side and also from secondary side what is the better side for change[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] على خلفية طلبات شركات الاتصال في المملكة العربية السعودية في الفترة الاخيرة للوحات توزيع للجهد المستمر DCDB فان هذه الطلبات كانت مشروطة باستخدام قواطع تيار مستمر ذات تيار منخفض 10A[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س : هل من الافضل الاستغناء عن هذه القواطع بفيوزات حماية واللتي تعد ارخص ثمنا بكثير من قيمة القواطع علما انه من الشائع استخدام الفيوزات في حماية هذا النوع من الشبكات ذات التيار المستمر , وهل الحماية بالفيوزات افضل من الحماية بالقواطع ام العكس صحيح .[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] من المعروف بان التصميم الداخلي لقاطع التيار المستمر لا يختلف ابدا عن تصميم القاطع العامل بالتيار المتناوب اي انه يمكن استخدام قاطع التيار المتناوب في دارة التيار المستمر لكن الفرق هو في التيار الاسمي المسجل على القاطع حيث انه عندما يكون التيار الاسمي المسجل على قاطع التيار المتناوب 16 امبير مثلا فانه عند استخدام نفس القاطع في دارة التيار المستمر فان هذا القاطع يفصل عند تيار مختلف عن التيار المسجل عليه [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] لهذا ارجو من الاخوة الكرام افادتي اذا كان هناك اي قاعدة او عمليه حسابية تشرح هذا الفرق وكيفية حسابه للتمكين من استخدام قواطع التيار المتناوب في دارة التيار المستمر [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ماهو الفرق بين التعريفين Icu و Isc ؟[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] حسب المواصفات القياسية IEC 947-2 : [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] Icu هو التيار الاعظمي لفصل (قطع) القصر وهي (القيمة الاعظمية لاستطاعة القطع) التي يتحملها القاطع لمرة واحدة ويقوم بفصل تيارها,[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] اما Isc فهو التيار التشغيلي لفصل (قطع) القصروهذه القيمة هي نسبة مئوية من Icu :[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] Isc = 100, 75 , 50 , 25 % Icu [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] التي يتحملها القاطع ثلاث مرات متتالية يفصل بينها زمن قدره ثلاث دقائق .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وكلما زادت نسبة Isc من Icu زادت معها قدرة القاطع على تحمل تيارات قصر عالية القيمة ولعدة مرات.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وبالتالي فان القاطع ذو سعة القطع Isc = 100% Icu يوفر اعلى معدلات الامان واستمرارية التشغيل.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ماهي خواص غاز SF6 الفيزياوية والكيمياوية؟؟؟؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يستخدم غاز (SF6) بشكل واسع في المعدات الكهربائية كعازل جيد للأجزاء الحية من الاجهزه وكوسط فعال في إطفاء الشرارة الكهربائية في غرف قواطع الدورة لمستويات الفولتية العالية . [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ولوحظ على مدى استخدامه كفاءته في العزل, أضافه إلى صغر حجم المعدات وانخفاض في كلف التصنيع والصيانة.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الخصائص[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] غاز SF6 عديم اللون والرائحة غير قابل للاحتراق.[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] غاز ثقيل أثقل من الهواء خمس مرات . كثافته m^3 / 6.14 KG في الضغط الجوي .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 3. درجه الانجماد C- 63.8[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 4. درجه الحرارة ألحرجه 45.46 C[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 5. الضغط الحرج 73.193 bar [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 6. الكثافة الحرجة 0.725 g / m^3[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 7. كثافة الغاز السائل عند درجة حرارة -50.8C …1.910g/m^3[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] لا يذوب في الماء ولكن يذوب بشكل جزئي في كحول الاثلين .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] 1. الوزن ألجزيئي 164.07[FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 2. درجه حرارة الميوعه - 50.8 C[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الخصائص الكيميائية .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يتكون غاز (SF6) من اتحاد عنصري الفلور والكبريت باختزال الحرارة المشعة من التفاعل.[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] > 2SF6 + 524 Kcal-------- S2 + 6F2[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] نظرا لاختزال كميه كبيرة من الطاقة يكتسب استقرارية عالية في خصائصه الكيمياويه والحرارية , ولوحظ عدم تأثره بالعناصر ألتاليه( هالوجين , بورون , كاربون , والحوامض الهيدروجينية (امونيا , بوتاسيوم ))[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] في درجه الحرارة العالية ( 500 C ) أو تعرض الغاز إلى تفريغ كهربائي يحصل تفكك في [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] الاصره الرابطة لجزيئات الغاز وينتج[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] معظم هذه الغازات تتفاعل مع الماء لتكون حامض الهايدروفلورايد في حاله وجود الأوكسجين والماء.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] عند التفريغ الكهربائي يتكون غاز (SO2F2) وغاز(SOF2) وتتميز هذه الغازات بخطورتها لجسم الإنسان لكونها سامه.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] مخاطر الغاز . [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] غاز ( SF6) لا يشتعل ولا يساعد على الاشتعال وغير سام في حالته الاعتيادية لكونه غاز خامل لكنه يسبب الاختناق عند تسربه من المعدات الكهربائية في ألاماكن المحصورة وذلك لاختزاله لغاز الأوكسجين إلى الأعلى . أما نواتج احتراق الغاز لها تأثير سام على الجهاز التنفسي.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]S2F, F.F2,F4 F10[/COLOR]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] استخدام الغاز في قطع الدائرة الكهربائية. [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] كما هو معروف إن التفريغ الكهربائي يحدث بين قطبين مختلفين بالشحنة حين حدوث انفصال أو توفر وسط ناقل للشحنة الكهربائية. هذه الظاهرة تحدث عاده في المعدات الكهربائية ( الفواصل- المفاتيح الكهربائية- قواطع الدورة ) وتسمى هذه الظاهرة Electrical arcing) ) التي من خلالها ترتفع درجه حرارة الوسط إلى درجه عالية والتي يجب خفضها بأسرع وقت لتفادي أي تلف في أجزاء الموصلات ألناقلة للتيار. لذا التجأ المصنعون إلى استخدام غاز (SF6 ) لقطع الشرارة لمواصفاته العازلية العالية .[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] عند حدوث تفريغ كهربائي وارتفاع درجة الحرارة يحدث تحلل في جزيئه الغاز إلى نواتج ومنها .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 2-Sulfuric Anhydride [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 3-Hydroflouric Acid [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 1-Sulphured Hydrogen[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] المشاكل ألعمليه في قواطع الدورة المستخدمة لغاز SF6 . [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] من خلال البحوث والدراسات حول مشاكل قواطع الدورة لوحظت إن ظاهره الرطوبة في الغاز هي المشكلة الرئيسية لهذا النوع من القواطع لما لها تأثير في تكوين المركبات ذات التأثير في خفض مستوى العازلية في الوسط العازل لقاطع الدورة [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] تأثير الرطوبة في غاز SF6. [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] غاز (SF6) مستقر جدا وله عازليه عالية يصبح غير مستقر عند احتوائه على نسبه من الرطوبة أعلى من المستوى المسموح حيث يؤدي إلى انخفاض مستوى ( with stand voltage) وترتبط هذه الخاصية بضغط الغاز ودرجه الحرارة للغاز . حيث عند تكاثف قطرات الماء على سطح المعدة الحاوية للغاز فان مقدار جهد الانهيار [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] (Break down voltage ) تقل بصوره كبيرة .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] أما عند تكثف الرطوبة على سطح العازل بصوره صقيع وليس كقطرات ندى فان معدل جهد الانهيار سوف لا يقل.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ولكي نمنع انخفاض مستوى ( withstand voltage) على طول سطح العازل,[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] فان(partial pressure of moisture ) يجب السيطرة عليه بحيث إن عمليه تكثف الماء بصوره قطرات رطوبة لا تحدث. وهذا يعني إن ( Dew point of moisture) في غاز ( SF6) يجب الحفاظ عليها بحيث تبقى تحت درجه الصفر المئوية. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] كما إن وجود الماء يؤدي إلى ظهور مواد ومركبات أخرى كما سبق . [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ولوحظ من خلال التجارب إن تحلل الغاز خلال فتره الخدمة الفعلية لقواطع الدورة هي ذات كميه قليلة جدا.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] السيطرة على حدود الرطوبة في غاز SF6.[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يمكن السيطرة على تأثير الرطوبة. [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] 1- تجنب انخفاض مستوى ( withstand voltage) على طول سطح العازل بالحفاظ على Dew point of moisture)) في غاز SF6)) اقل من درجه الصفر المئوية وهذا يمنع تكثف الرطوبة على سطح قاطع الدورة بشكل قطرات.[FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 2- كيمياويا . إن مستوى الرطوبة يجب أن يحسب بحيث إن عمليه التفاعل الكيمياوي نتيجة إخماد الشرارة لا ينتج منه مركبات ضاره.[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] * أسباب وجود الرطوبة في غاز SF6 .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 1- عدم التخلص من الرطوبة بصوره نهائيه أثناء التصنيع أو عند التجميع. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] * طرق السيطرة على الرطوبة في غاز SF6. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ---------------------------------------------- [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] إن الطرق العملية للسيطرة على الرطوبة المحتواة في قواطع الدورة المعزولة بالغاز يمكن تلخيصها : [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ا / اختبار مواد العزل العضوية والتي لها خاصية قله الامتصاص للرطوبة.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ب/ تجفيف حاويه الغاز أو قاطع الدورة وعمليه التجفيف يمكن القيام بها بعمليه ( nitrogen purring ) أو الهواء الساخن مع الاحتفاظ بالتفريغ الكهربائي قبل إملاء القاطع بالغاز . [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ج/ اختبار ماده ( ( O-ring .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] د/ استخدام المجففات لامتصاص الرطوبة .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] إن اختبار كميه ونوع المادة المجففة لامتصاص الرطوبة من غاز (SF6) يعتمد على عوامل يجب مراعاتها لمعرفه مقدار المادة المجففة ومنها [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] :-[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 1- امتصاص كميه الرطوبة النافذة خلال أل (sealing) من الخارج خلال الفترة بين الصيانة المثالية.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] 2- امتصاص مقدار الرطوبة المحتواة في غاز (SF6) المستخدم . [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] 3- امتصاص كميه الرطوبة الممتصة أثناء عمليه التفاعل والتركيب . [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]… …[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]

[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue]2- تبخر الرطوبة من المواد العازلة من أسطح حاويات الغاز أو قواطع الدورة أثناء التركيب . 3- نفاذ الرطوبة من خلال فواصل قواطع ألدورة (Rubber sealing) الرابطة للأجزاء المختلفة.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ويجب اختيار موقع مناسب للمادة المجففة داخل القاطع [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] منع تكثف الرطوبة في قواطع الدورة. [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] من المعروف إن غاز (SF6) يتحول إلى حاله سائله بوجود ضغط عالي وانخفاض في درجة الحرارة . حيث في درجة حرارة الصفر المئوية وضغط 12 كغم / سم2 يتحول إلى سائل . لذا يجب رفع درجه حرارة الغاز والعمل على بقائه في منطقة الغاز . ومن التجارب الميدانية على قواطع الدورة ذات ضغط فائق 400 KV وباستخدام مسخنات 2 KW ومراوح تهويه وفي مناخ بدرجه -22 C وبعد إجراء الفحوصات لوحظ خلو الغاز من الرطوبة وعدم تأثره في هذه الدرجات .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] *تسرب الغاز نتيجة الأعمال النهائية لسطوح العازل . [/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] من الضروري جدا ملاحظه معامله سطوح العزل لغاز( (SF6 والحدود المسموح بها وعملية اختيار نوع أل ((O- ring المناسب حيث تم إجراء فحوصات عديدة على مختلف أنواع ((O- ringولوحظ أن ((O- ring المصنع من مادة (Silicon rubber)يتأثر باختلاف درجة الحرارة والعوامل الأخرى . لذا استبعد من استخدامه في قواطع الدورة ولوحظ إن أل ((O- ring المصنوع من مادة (neoprene) له خواص جيدة أفضل من السابق ولذا انتشر استخدامه .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وماهي معادلة حساب ال (DEW POINT )[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] لغرض حساب ومعرفة نقطة التندي للغاز(DEW POINT )[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] يجب توفر جهاز لقياس نسبة الرطوبة في الغاز (Hygrometer ) حيث بالإمكان معرفة درجة الحرارة لذلك الغاز تحت ضغط معين كما يجب أن يكون لدينا جدول معياري للغاز يوضح العلاقة بين الضغط ودرجة الحرارة ونسبة الماء إلى الغاز بالحجم [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] باستخدام المعادلة التالية يمكن معرفة نسبة الماء إلى الغاز بالوزن ( ppmw ) والتي عن طريقها يمكن معرفة هل إن عدد الجزيئات ضمن الحدود المقبولة أم لا حيث إن القيمة المقبولة هي (15 )او اقل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] }PPmw = PPmv x ( mw. water / mw.gas){[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] PPmw = PPmv / 8.1 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] حيث-----------[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] PPmw ---------- جزء من مليون بالوزن[FONT=Comic Sans MS][SIZE=2][COLOR=Blue] PPmv ---------- جزء من مليون بالحجم mw water ---------- الوزن المولاري للماء = 18 mw gas ---------- الوزن المولاري للغاز = 146.05 لغاز SF6[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ماهي الاقفال المتداخلة اليدوية والكهربائية؟؟؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] نظام حماية يستعمل لتلافي التشغيل الخاطيء للمعدات للحفاظ على سلامة الأشخاص و المعدات. وبمعنى آخر انه لايمكن تشغيل جهاز مالم تتم الشروط الصحيحة للتشغيل.فمثلا لايمكن فتح الفاصلة الهوائية عندما يكون قاطع الدورة في حالة توصيل (ON) كذلك لايمكن غلق قاطع الدورة والفاصلة مفتوحة (OFF) . كما لايمكن غلق عتلة التأريض والفاصلة في حالة (ON) كما لايمكن غلق الفاصلة الهوائية وعتلة التأريض بالعمل (ON) .[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] a – الأقفال المتداخلة الميكانيكية (اليدوية)[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وفيها تكون عملية التداخل بواسطة عتلات ميكانيكية أو مفاتيح يتم رفعها باليد. يمكن أن يكون هذا النوع عتلة تمنع التشغيل والإطفاء أو مفاتيح يتم تحريكها ونقلها بين منطقتين.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] وفيها تتم عملية المنع من التشغيل أو الإطفاء عن طريق ملامسات كهر بائية (auxiliary switch)تقوم بعملية قطع وتوصيل في دوائر السيطرة والتحكم أي أنها عبارة عن أقفال مركبة ميكانيكية وكهر بائية. b – الأقفال المتداخلة الكهربائية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] لماذا ينصح بربط شبكة الحماية من الصواعق مع شبكة التاريض الخاصة بالمنشات الصناعية ؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] عند نزول تيار الصاعقة العالي جدا والذي قد يصل إلى 100 كيلو أمبير في بعض الحالات ضمن نوازل شبكة الحماية التي تفرغه إلى الأرض يتولد حول هذه النوازل فيوض كهرومغناطيسية تتشابك مع خطوط التغذية الكهربائية وخطوط التاريض للتجهيزات المختلفة فتولد فيها جهودا تحريضية تتناسب مع تغير شدة التيار وزمن استمراره, لذلك ينصح بربط شبكة الحماية من الصواعق مع شبكة تاريض المبنى, ويجب أن لا ننسى ربط وصلات تساوي الكمون لأنها لب الحماية الداخلية من الصواعق حيث يجب أن لا يحدث أي فرق في الكمون وهذا الفرق هو الذي يشكل خطرا على الأشخاص والممتلكات في حال حصوله,[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ويجب ربط كل الأجزاء المعدنية من البناء بشكل مباشر والنواقل الفعالة من المنظومة الكهربائية بشكل غي مباشر مع حلقة ربط تساوي الكمون.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ويؤكد النورم الألماني : DIN VDE 0100, part 410, section 6.1.2 بأن على منظومة ربط تساوي الكمون الرئيسية أن تضم الأجزاء الناقلة التالية:[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - خطوط الحماية الرئيسية (مثلا ناقل PEN في منظومة الشبكة من نوع TN ) للتغذية الكهربائية العادية بالتوتر المنخفض.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - الناقل الأرضي (مثلا عروة الربط للأرضي الأساسي)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - الخط الأرضي للحماية من الصاعقة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - أنابيب المياه الرئيسية [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - منظومات الأنابيب المعدنية الأخرى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] - كما يجب أن تربط مع منظومة ربط تساوي الكمون جسور الرافعات وأغلفة الكابلات المعدنية وحوامل الهوائيات ومنظومات الاتصال.[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] ويجب لن لا ننسى ربط كل النواقل الفعالة مع منظومة ربط تساوي الكمون عبر موقفات تيار الصاعقة lighting current arresters[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] س: ماذا تعرف عن ال ANSI DEVICE NUMBERS ؟[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2][COLOR=Blue] هى عباره عن ارقام ثابته تعبرعن انواع مختلفه من الحمايات كالتالى:[/COLOR][/SIZE][/FONT] [FONT=Comic Sans MS][SIZE=2]
[/SIZE][/FONT] [/CENTER]

(مهــ نور ســة) #3

س : ما هيأهمية (Tertiary Winding) في المحولات؟
ج: ال Tertiary Winding
فىالمحولات هى ملف ثالث فى المحول بالإضافة إلى
الملفاتالإبتدائية و الثانوية و يوصل على هيئة دلتا ويستخدم لمرورمركبةالتيار الصفرية
في حالةعدم إتزان الأحمال على المحول و يستخدم لإنتاج جهدثالث للمحول ويختلف قيمةالقدرة على هذا الملف عن الملفين الرئيسين و فيكثير من الأحيانتكون قدرتها ثلثقدرة الملفات الأخرى,
و فيأحيان أخرى لا يتم إستخدام هذا الملف لإنتاج القدرةولكن لمرور مركبةالتيار الصفريةفقط.
س: مافائدة التيار المستمر في المحطات ؟ وكيف يمكن الحصولعلية ؟
يمكنالحصول على التيار المستمر من مصدرين
.1الشاحنة : في حالة وجود التيار المتناوب
.2 النضائد ( البطاريات ) :عند عدم وجود التيارالمتناوب

الفوائدمن التيار المستمر
.1الفصل والتوصيل من داخل السيطرة
.2الحمايات
.3الاشارات
4. لاضاءةالاضطرارية
س: ذا عندسحب الكابلات يجب شدها من الغلاف الخارجي او طبقة Armoury ؟
عند سحبالكابلات يجب شدها من الغلاف الخارجي او طبقة Armoury ولايتم شدهامنالموصل اوالعازل
ان تمشدها من الموصل سوف يتم استطالة للموصل وتقل مساحةمقطع الكابلوبذلكيقل تحمل الكابل
للتياروخاصةIs.c
اما ان تمشد الكابلات من العازل فهذا يؤدي الي قلة isolating وقصرعمره
س: عرفظاهرة الهالة الضوئية (Crona Discharge)
ج: هىسماع صوت أزيز و شم رائحة الأوزون و مشاهدة ضوء أزرقباهت
حولالموصل و كأنه يتوهج و من العوامل التى تساعد على ظهورههي :
.2الشابورة المائية
.3درجة نظافة العوازل
.4عدم التربيط الجيد للمهمات
و تحدثهذه الظاهرة نتيجة تحرك الإلكترونات للموصل واصطدامها
ببعض فيحالة خطوط الضغط الفائق و يصحب هذه الظاهرة فقد فيالطاقة الكهربية
1. درجةرطوبة الجو
س : ما هيمحولة التاريض ؟
وهي عبارةعن ملف تربط في حالة ربط احد ملفات المحولة دلتاوذلك للحصول علىنقطة الصفر ( الخط البارد )
س: ايهمااكثر تحسس للعارض الوقاية التفاضلية ام وقايةالارضي المحصور ؟ولماذا؟
وقايةالارضي المحصور تكون اكثر تحسسا للعارض من التفاضلية .
وذلكلانها لاتحتوي على ملفات ممانعة
س: مافائدة الخزان الاحتياطي في محولات القدرة ؟
3. التحكم بالزيت من التقلبات الجوية .حيث انالزيت يتمددصيفا ويتقلص شتاء
1. تقليلالمساحة السطحية للهواء الملامس للزيت . 2. تعويضالخزانالرئيسي في حالة النضوح (Look Out)
س : ما همانواع الصوهرات الموجودة (fusible ) و اين يستعملكل نوع؟
ج:يوجدنوعين من صهورات و هما :
1-الصهورةمن نوع AM و هو يستعمللحماية الحمولاتالعاديةالتى ليس لهاتغير كبير فيتيار حمولة مثل مقاومات لتسخين لاجهزوالكترونية عامة . 2-الصهورة من نوع GL و هي تستعمل فيالحمولات التى التييتغير تيارحمولاتها بشكلكبير مثلا الصهورة تتحملل تيار البدا بنسبةللماكناتالكهربائية بينماالصهورة من صنف AM تنصهرعند تيار البدايه
س :لماذايجب عزل Bus Bar Protection من الخدمة أثناءإختبارأىدائرة؟
عند فصلالدائرة لعمل إختبارات Current Injection والمفتاحوالسكاكين فىحالة الفصل تكونالإشارة بالوضع لخروج هذة الدائرة منالخدمة قد إتخذتوقاية القضبانإستبعادها من حسابات الإتزان للبسبار.
وعندإجراء عملية الحقن بالتيار تمر قيمة تيار الحقنبالوقايةالتفاضليةللقضبان والتى يستشعر بها مما يؤدى الى عدم إتزانةويعطى أمرا فوريابفصلجميع المهمات
ما هو ATS ؟
هو نظاميستخدم في توليد القدرة الكهربية (AC)
وهو عبارةفي الغالب عن محرك ديزل يتصل به Alternator والذيبدوره يحولالطاقةالميكانيكيةالى كهربيةac ويمتاز هذا النظامبإمكانيةتركيبةعلىالسيارات العاديةمع مراعاة وجود دائرة rectifier ودائرة matching وذلكلتحويل ac to dc كما يمتاز alternator بقدرته على إنتاجالقدرة المطلوبةوذلك فقط بمجردتشغيل المحرك وذلك عكس المولدات العاديةفي السيارات(دينمو) والذييتطلب رفعقدرة المحرك وبالتالي ترتفع قدرةالدينمو على الإنتاج.
ما هو سببارتفاع سعة الفصل في قواطع الدائرة كلما انخفضتالفولتية؟
كلماانخفضت الفولتية قلت الشرارة المتولدة عند عملية الفصلوبذلك ترتفعسعة الفصل.

سؤال: مافائدة ربط الخط الرابع (الارثر) عند ربط الملفاتبطريقة الستارCOLOR=blue[/color]؟
الجواب: وذلك لتمرير التيارات الزائدة جراء عدم الموازنةبالحمل.

ما هيمناولة فوق التيار لنقطة التعادلNeutral Over Current Relay
تعتبرهذهالمناولة كحماية إسناد جاهزة (Buck up Earth Fault ) للعمل فيحالة فشل مناولة الاتصال الأرضي (E/F Relay ) من فصل قاطعالدورة للمغذي أوالمحولة عند حدوثاتصال ارضي لأحد الأطوار مع الأرض كماوتعمل هذهالمناولة كحمايةعند حدوث اتصال ارضي داخل المحولة او علىالقابلو الواصلبين المحولةوقاطع الدورة الخاص بالمحولة الخاص بالمحولةوعند اشتغال هذهالمناولة تعملعلى فصل المحولة من الجهتين (KV 33 (11 KV - ويتم نصب محولةالتيار على نقطةاتصال نقطةالتعادل للمحولةبمقاومةالخطأ الأرضيبالأرضلتحسس أي تيار خطا ارضي راجع للمحولة .
س:ماهىانواع الحماية الضروية للمولد؟
بالنسبةللحماية المولدات هناك حمايتان اساسيتان هما
E / F التماس الارضي
الوقايةالمذكورة هى وقاية احتياطبة اما الوقاية الاساسية اوالرئيسية فهىالوقايةالتفاضلية
over current
س : ما هىالإجراءات التى يجب عملها لتغيير أى عداد قياسللتيار أو وقاية - والدائرة بالخدمةوبحمل كبير - ويمر التيار بجميعدوائرها الثانوية ؟
ج: يتمعمل قصر Short قبلوبعد العداد (Link ) حتى يمر بهالتيار(المسارالجديد) وبعد ذلكيتمقياس التيار المار فى ال (Link ) للتأكدمن سلامةإغلاقالدائرة
- ويتم رفع العداد أو جهاز القياس أو الوقايةبعد تمام عزلهمن الخدمةبالطريقة السابقة

لماذايستخدم في منظومة القدرة الكهربية نظام الثلاثة اوجهوليس4او5ال6؟؟
يفضلاستخدام نظام الثلاثة اوجه للاسباب الاتية:
1- لقلةالتوافقيات في نظام الثلاثة اوجه
2- قلة التكلفة الاقتصادية. 3- امكانيةتوصيلة نجمةودلتا للحدمن تيار البدء.
س:ماذاتعرف عن الharmonics
آلمشآكلالناتجة عنها- :

(مهــ نور ســة) #4

[FONT=Comic Sans MS][SIZE=2][COLOR=blue]
[/COLOR][/SIZE][/FONT][CENTER][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]السلامعليكم[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مجموعة من[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الاسئلة اللي اكيدراح تفيدكم بمجال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الهندسةالكهربائية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ان شاء[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الله الكل يستفاد منهه[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س : ما هو[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الفرق الجوهري بين محولات الفولتية و محولات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ج : الفرق[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الرئيسي الجوهري ان محولات الفولتية تصمم للعملعلى قيض مغناطيسيثابت )وبالنتيجة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]على فولتية ثابتة), في حين ان محولة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار تصمم للعمل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]على فيض مغناطيسي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]متغير داخل الحديد[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وبالنتيجة على جهد متغير يتناسب مع تيار الحمل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue])[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: ماهى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الطريقة ا لحماية باستخدام ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]directional relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وهذه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الطريقه غالبا يستخدم معها[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Over Current Relay [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]هى تحمى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المنطقه الموضوع عليها ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]من حدوث اى خطاء[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] (Fault) [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فىالدائره[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فنجد ان[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فى الحاله العاديه يمر التيار فى فى الاتجاه العادىللدائره ولكنعند حدوث اى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] (Fault) [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فان[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]اتجاه التيار ينعكس[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وباتالى يمر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]اتجاه ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فيقوم[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]Relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بفصل ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] C.B[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ويوجد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]نوعين من ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]directional relay [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] -1[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النوع الذى يستخدم معه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] over current relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وهذا النوع يفصل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بعد انعكاس[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار وزيادته[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]عن التيار المقنن[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وهذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النوع يفصل لحظيا بعد انعكاس التيار فيه ويستخدم لحمايهالمولدات فىحالته وجود[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مولدين على نفس ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] bus bar[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] Directional relay [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تستخدم فى حمايه ال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Bus Bar-Generators -Transformer Instantaneous directional relay -2 [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س : ماهي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الحماية المصاحبة لحماية القضبان التفاضلية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]Bus Bar Differential Relay [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ج: حماية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الاشراف الفولتي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Voltage Supervision Relay [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: ماذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يعنى لك الرمز[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] HVHRC[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ج: هذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الرمز إختصار لــ[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] High Voltage High Rupturing Capacity fuse [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وهو[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يستخدم فى لوحات الجهد العالى لحماية المحولات ولوحاتالمكثفاتوالمحركات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]والكابلات التى تعمل على الجهود العاليه ، ويتمإختيار الفيوز منالجداول طبقاً[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لسعة أو قدرة المعده والجهاز المراد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]حمايته والمقابله[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لخانةجهد التشغيل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س:ما هي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أنواع الحماية المستخدمة للمولدات؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] (Generator protection)[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 1-Overcurrent protection[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 2-Under/Over voltage[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]3-Reverse power[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]4-Loss of excitation[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]5-Rotor Earth leack[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]6-Differencial Protection [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 7-Negative sequence current[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 8-Netral Point Voltage[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 9-Out of Step[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]10-over/under Frequency (speed)[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]هذه أشهر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أنواع الحماية المطبقة في المولدات التي تحافظ علىكفاءة المولدوالجزء الذي يعطي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الحركة للمولد[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: لماذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يجب قصر طرفي محول التيار عند عدم اتصالهما بحمل؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يستخدم[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]محول التيار للحصول على تيار صغير بقيمة متناسبة معتيار آخر كبيرالقيمة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لاستخدامها في أجهزة القياس والحماية. ويتم ذلكلثلاثة أسباب[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]:[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الأول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]: [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تجنب الحاجة إلى قطع دائرة التيار الكبير والتي تكونفي صورة موصلاتذات مقطع كبير[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]كابل – خط هوائي – قضبان عمومية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] Bus bars… [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]إلخ) من أجلقياس التيار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الثاني[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]: [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]استخدام أجهزة قياس وتحكم صغيرة ذات مقننات جهدوتيار منخفضة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يسهلالتعامل معها[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]. [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الثالث[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]: [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التوحيد القياسي لأجهزة القياس والحماية. وبذلكتستخدم نفس[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الأجهزةالصغيرة الحجم لنطاقات متعددة وعالية من قيم التيارالكهربي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وقد يكون[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الأمر مضحكاً إذا تخيلنا محاولة قياس تيار كهربييُقدر بمئات أوآلاف الأمبير يمر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]في كابل سميك باستخدام جهاز أميتر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تقليدي بوضعه على[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التوالي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]!!![/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النظرية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الأساسية لعمل محول التيار لا تختلف عن محول الجهدبأنواعه العديدة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]قدرة – توزيع[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] - [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]قياس… إلخ) والاختلاف هو في مستوىتيار المغنطة. فيمحولات الجهد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يتناسب تيار المغنطة في محول معين معالجهد المسلط علىالابتدائي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مقداراً وتردداً). ونظراً لأن العمل غالباًيكون عند مستوى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ثابتلجهد الابتدائي فإن تيار المغنطة يظل ثابتاً معمختلف ظروف العمل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ولايتأثر بشكل كبير بظروف الحمل (بداية من اللاحملوحتى الحمل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الكامل). ويمثلتيار المغنطة مركبة من تيار الابتدائي. وفيمحولات الجهد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يتميز تيارالابتدائي بالمرونة حيث تتغير قيمته حسب معاوقةالحمل في[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الثانوي، ويصل إلىأدنى قيمة عند اللاحمل (فتح دائرة الثانوي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]) [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]في محول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار تتحدد قيمة تيار الابتدائي (المار في الكابلأو الخط أوالقضبان[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]العمومية…إلخ) حسب ظروف الشبكة ولا دخل لتيارالثانوي في قيمته[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]على عكس محول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الجهد). أي أن تيار الابتدائي مستقل عنظروف المحول بما[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فيهاظروف دائرته الثانوية. يقوم معظم تيار الابتدائيبإنتاج الفيض[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المغناطيسيفي قلب المحول الذي يقوم بتوليد قوة دافعةكهربية في ملفات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الثانوي. أيأن[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تيار الابتدائي يمثل (في[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أغلبه) تيار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المغنطة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يقوم تيار الحمل (فيالثانوي) بمهمة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]إنتاج فيض مغناطيسي معاكسلفيض الابتدائي مما يُحد من الفيضالمحصل وبالتالي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]من الجهد على طرفيالملف الثانوي. وفي حالة عدم اتصالدائرة الثانوي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لمحول تيار بحمل معبقائها مفتوحة فإن تيار الثانوي ينعدم،وينعدم معه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التأثير المضاد للفيضالمغناطيسي الكبير الناتج من تيارالابتدائي ذي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]القيمة العالية (أوالعالية جداً). وحينئذ يرتفع فرق الجهدبين طرفي الثانوي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المفتوحين) إلىمستويات كبيرة جداً قد تصل إلى الحد الذييسبب مخاطر كبيرة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لكلٍ منالمحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أو للشخص المتعامل معه أو للمُعدة التيتحتوي المحول أو[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المجاورةله. كما يتأثر القلب الحديدي للمحول في هذهالحالة بالقيمة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]العالية جداًللفيض المغناطيسي بما تسببه من تعرضه للتشبعالشديد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وكذلك[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مستوياتعاليةمن الحرارة الناتجة من[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيارات الدواميةوالتخلف[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المغناطيسي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]. [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ملاحظـــة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]عملية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أثناء[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]عملي في إحدى شركات البترول قام أحد الزملاء – عن غيرقصد- بفتحدائرة الثانوي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لمحول تيار أثناء فحصه لدائرة تشغيل وتحكممعقدةلأحدالقواطع. وكانت[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النتيجة إصابة الزميل بحرق في يده نتيجة لماوصفهبأنه يشبهناراً تخرج[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]من جهاز[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]للحام[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: ما هى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النسبه بين مقطع الكابلات الارضيه و الموصلاتالهوائيه فى خطوطالجهد المتوسط؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]النسبه هى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] 2 : 1 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]اى عندما يكون مقطع الهوائى 35 / 6 يكونمقطع الكابل 3[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] * 70[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 70 / 12 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يكون[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مقطع الكابل 3 * 150[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] 150/24 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يكون[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مقطع[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الكابل 3[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] * 240[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: لماذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يوصى دائما بالتحقق من الربط الجيد للموصلات معالقواطع وغيرها؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لأنه فى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]حالة الربط غير الجيد يتكون فراغ هوائى فى هذهالمنطقه يكون[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]قابلللتاين مما ينتج عنه مايعرف بالتخمر اى يحدث اشتعال فىهذه النقطه[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ما هي[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الطرق المستخدمة لتقليل تيار البدء فى المحركات؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ج : من[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الطرق المستخدمه لتقليل تيار البدء للمحركات التىتعمل على جهودصغيره[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] 2. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]توصيله نجما دلتا[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المحركات التى تعمل على جهد متوسط[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]استخدام[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]مقاومه عند بدء تشغيل المحرك وتكون متصله مع العضوالدوار بالتوالىلتقليل التيار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الناتج[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] soft starter .1 [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: اذكر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]انواع التوصيلات لملفات محولات التوزيع وما الاكثراستخداما منها؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]دالتا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] /[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ستار وهي الاكثر استخداما[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ستار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] /[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]دلتا[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ستار[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] / [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ستار[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]دالتا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] /[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]دالتا[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: ماذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يحدث لمحولة فولتيةعند تماس احد الاطوار الثلاثةوبقيت في العمل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]. [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وكم الوقت[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المستغرق[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]للحدث ؟ ولماذا؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تنفجر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]خلال ( 50دقيقة) من حالة بدء التماس وذلك لان الفولتيةتنتقل منالطور الذي حدث[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فيه العارضا الى الاطوار السليمة مما يؤدي الىارتفاعالاطوار السليمة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ضعف قيمتها تقريبا[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: لماذا[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ينصح دائما بتأريض خطوط الضغط العالي عند العملفيها؟[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جـ : حتى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يتم تفريغ التيارات السعوية الموجودة في مللفاتمحولات التوزيعوخطوط النقل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]والتي تتحول الى لمكثفات سعوية تفرغ شحنتهافي الشخص الملامسلها وقد تصيبه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بصاعقة كهربائية اذا لم تؤرض الخطوط[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]اويتم عمل شرت (جمبر[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] )[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بين الخطوط[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] *[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وحتى اذا ماقام احد العاملين باعادة الخط[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]اثناء العملبطريقة الخطأفأذاكان الخط مؤرض[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فأنه لايقبل الاعادة[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]وذلك[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]للحفاض على سلامة العاملين في صيانة الخطوط[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س:ما هو[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقايه؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]هو جهاز[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ميكانيكى او الكترونى او رقمى يقوم بملاحظة وقياسالقيم الطبيعيهللشبكه من جهد او[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تيار او درجة حراره او تردد او ضغط وفىحالة اختلاف هذهالقيم عن[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المعدلات الطبيعيه سواء كانت[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بالزياده[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]او بالنقصان حسب طبيعة ونوع العطل فان جهاز الوقايهيقوم باعطاءامر كهربى الى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المفاتيح[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الخاصه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]بالمعده التى حدث عليها هذا القصر وبذلك يتم عزلها منالشبكه وفىاسرع وقت ممكن[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]س: ما هى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أجهزة الوقاية الموجودة على محولات القدرة ذاتالقدرة العالية؟[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ج: أجهزة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الوقاية الموجودة على المحولات[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]:[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .1 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية التفاضلية: هو جهاز نطاق حمايته[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المنطقةالموجودة بين[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]محولات التيار للجهود المختلفة و[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يقوم الجهاز بالمفاضلة بين[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التياراتالداخلة و الخارجة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار التفاضلى)فإذا كانوامتساويان فىالوضع المتزنفأن المحول سليم[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]أما إذا كان هناك عطل داخل المحول فإن قيمةالتيارالتفاضلى له[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]قيمة(أي و جود عطل داخل المحول) فيفصل المحول ويمنعمنعاًباتاً توصيل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]إذا إشتغلت هذه الوقاية إلا بعد الكشفعلىالمحول ومعرفة سبب[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الإشتغال و هناك عدة عوامل يجب أخذها فيالإعتبار مثلمغير الجهدو تغذية العطل من[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]إتجاه واحد أو أكثر و عدةعوامل أخرىو هذاسوف نتناولهلاحقاً[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .2 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية ضد زيادة التيار و يعمل بزمن و[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]تكون وقايةظهرية للوقاية[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التفاضلية[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .3[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية ضد التسرب الأرضى و يغذي من نقطة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التعادلالمجمع لأوجه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]التيار من محولات التيار[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .4 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية ضد التسرب الأرضى المحدد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] ([/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المقيد) و يركبلحماية المحول منالتيارات الصغيرة[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المارة في نقطة التعادل ( الملف[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الموصل ستار في المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue])[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .5[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية الغازية و يعرف بالبوخلز ريلاى و[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يعمل إذاإرتفعت درجةحرارة الزيت داخل المحول و تصاعد أبخرة منه[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يعطى إنزار بوجودخطأ بالمحولأما إذا كان هناك[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]قصر داخل المحول فإن الزيت يغلى و يصعدمنالتنك الرئيسىللمحول إلى التنك[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الإحتياطى مارا بالعوامة السفلى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]فيدفعها[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]في طريقه فيفصلمن جميع الجهات و[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يمنع منعا باتا توصيل المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]إلا بعد[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الكشف عليه و إذاكان الإشتغال[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]صحيح يتم إختبار المحول و الزيت[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .6 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز الوقاية ضد إنخفاض مستوى الزيت[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] (Low Oil Level)[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]و هويعمل عندإنخفاض مستوى[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الزيت عن حد معين يعطى إنزار حتى يتم تذويده[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .7 [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]جهاز ذيادة الضغط داخل المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue] (Oil Pressure Relief) [/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]ويعمل عند ذيادةالضغط داخل المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]لأى سبب فيقوم بضغط على بن فيفصل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT]
[FONT=Comic Sans MS][SIZE=2][COLOR=blue] .8[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الإرتفاع في درجة الحرارة و هو عبارة عن حساس[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]يحس بدرجةالحرارة داخل[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المحول و يوجد به 4 كونتاكات إثنين[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]منهم لتشغيل مجموعتين من[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]المراوح وإثنين واحد إنزار و[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue]الآخر يعطي فصل للمحول[/COLOR][/SIZE][/FONT][FONT=Comic Sans MS][SIZE=2][COLOR=blue].[/COLOR][/SIZE][/FONT][/CENTER]

(طه2) #5

شكرا جزيل على المجهود الطيبة منك الله يوفقك

(مهــ نور ســة) #6

منور اخي الكريم بردك

(rmka25) #7

شكرا جزيلا على هذا الجهد الرائع
اسئلة مهمة جدا ومن صميم الحياة العملية
اسئلة شاملة مثيرة للمعلومات منشطة للذهن
نتمنى لكم الموفقية والنجاح ودوام الصحة والعافية
جعلها الله في ميزان حسناتكم .

(مهــ نور ســة) #8

عفواا اخي الكريم
هذا واجبي بنقل اي معلومة تفيد الجميع

(Ahmed mahmoud mansour) #9

شكرا جزيلا على هذا الجهد الرائع

(مهــ نور ســة) #10

عفوااا اخي الكريم

(system) #11

شكرا على هدا الموضوع الجيد عندى سؤال اختى عندى فرن قوس كهربائى وتقابلنى مشاكل ويارب يطلع فى ايديكم ان تحلوها لى يوجد عندى مولد 500 كيلو فولت ومحول 400 كيلو وعمدان اجرافيت وكلما ابدا التشغيل يعمل لفترة قصيرة ثم تحدث اضرابات تطفى المولد لمادا وشكرا

(مهــ نور ســة) #12

هناك اكثر من احتمال اخي الكريم
1- المولد تكون فيه مشكله وقود او ماشبه ذلك
2- ان قدره الهاز اعلى من المولد وبذلك لا يتحمل
التشغيل الا لفتره قصيره
3- او هناك مشكله بالاسلاك اي لاتتحمل التيار العالي الذي
يمر من خلالها من المولد
4- او مشكله ميكانيكية في المولد